|Function 1:||Active Power Regulation||Function 2:||Fast Automatic Synchronization|
|Function 3:||Detection Of Electrical Fault||Function 4:||Increase Or Decrease Load And Load Operation|
|Function 5:||Guide Vane Opening||Function 6:||Adopt PID Intelligent Control|
|Keyword:||Hydro Turbnine Governor||Function 7:||Rated Oil Pressure 2.5-4.0mpa|
water generator parts
BYWT Series Microcomputer Is The Parallel Pid Type Hydro Turbine Governor Of The Controller For HPP
1. Kaplan turbine generators series.
2. Turgo turbine generators series.
3. Tubular turbine generators series.
4. Francis turbine generators series.
5. Pelton turbine generators series.
The BYWT series governor is a parallel PID type governor with a microcomputer as the controller, which is suitable for mixed flow, axial flow fixed type and rotary type turbines. Its main static and dynamic indicators have reached the domestic advanced level. The dual power supplies operate in parallel with the dual computer power supply. The 48 technical data communicate with each other within 20 milliseconds and multi-level automatic protection, which makes the governor highly reliable. The modular structure of the fully automatic system and components makes operation and maintenance extremely convenient, and the control program can be changed only by changing the software. It is easy to implement advanced control by networking with the instruction computer to realize computer control of the entire power station. Also suitable for the transformation of the old unit.
The routine inspection contents of the governor mainly include: ensuring that the governor working environment is clean and tidy, preventing dust from entering the hydraulic pipeline, affecting the normal operation of the hydraulic system; preventing the hydraulic oil from being affected by moisture, and the hydraulic oil is too high on the side Corrosion is caused, and once the hydraulic oil moves rapidly in the pipeline, a large number of bubbles are generated, which may result in poor oil passage and even overflow of hydraulic oil. Check the pilot valve for jamming. If it is found, it should be processed as soon as possible. During the operation, not only the motor action is frequent, but also whether the temperature change is within the specified range; check whether the components are installed firmly, whether the meter and monitoring screen indications are normal; check whether the values of the monitoring interface are consistent with the actual running status of the equipment; Whether the system has a fault alarm message is issued.
1. measure the frequency of the unit and the power grid, and realize the frequency regulation of the unit when it is running without load or in isolation;
2. when no load is on, the unit frequency automatically tracks the power grid frequency, which is convenient for rapid automatic synchronization;
3. manually start and stop, increase and decrease load, and operate with load;
4. automatically start and stop the machine, and automatically adjust unit output according to permanent slip (bp) after grid connection;
5. switch automatically and manually unconditionally and without disturbance;
6. main parameters and operation status of speed regulators such as machine frequency, network frequency, guide blade opening, manual and automatic are displayed on the display screen;
7. able to set the operating parameters of the governor through the display screen;
8. when an electrical fault is detected, it can be automatically cut to manual and the load can be fixed in the state before the fault.
9. high reliability programmable controller (PLC), small size, strong anti-interference ability, and an average trouble-free time of more than 300,000 hours;
10. software frequency measurement can meet the requirements of timing and accuracy of frequency measurement;
11. PID intelligent control, with good stability and adjustment quality
Q1, Which turbine should I choose?
Please tell me the water head, flow rate, frequency, Total power you need
, voltage, on grid or off grid operation, we will propose a solution.
Q2, Can your factory provide all the equipment for hydropower generation?
Yes, we can provide you with turbines, hydro-generators, pressure regulators, turbine wheels, control panels, transformers, monitoring systems and more.
Q3, Can you do EPC for a hydroelectric power plant?
Yes, we can provide TURN-KEY and EPC services including measurement, design, manufacturing, construction, manufacturing, commissioning, inspection, maintenance runner replacement and refurbishment/upgrade/improvement/repair/refurbishment of turbines/generators including bearings, seals For parts and key parts, we will send technicians and workers to install equipment.
Q4,Is your company a trading company or a manufacturer?
We are a manufacturer of hydro turbine generators and started to promote the international market in 2013. Our factory is located in Sichuan, where China's water conservancy and hydropower is most developed. Welcome to visit our factory in China.
Q5, What is an acceptable MOQ?
For this product, our acceptable MOQ is 1 set.
Q6,How long is the delivery time?
Delivery times range from 15 days to 6 months depending on the model you are purchasing.
Q7,Does your company have its own independent official website?
Of course, and we can see more information about our company and products on our official website.
website address: www.fstgenerator.com